TeSys F contactor - 3P (3 NO) - AC-3 - <= 440 V 115 A - coil 110 V ACShow more characteristics >
Main rangeTeSys product nameTeSys F product or component typeContactor device short nameLC1F contactor applicationMotor controlResistive load utilisation categoryAC-3AC-4AC-1 poles description3P power pole contact composition3 NO [Ue] rated operational voltage<= 690 V AC 50/60 Hz [Ie] rated operational current200 A (at <40 °C) at <= 440 V AC-1115 A (at <55 °C) at <= 440 V AC-3 motor power kW55 kW at 380...400 V AC 50/60 Hz (AC-3)59 kW at 415 V AC 50/60 Hz (AC-3)59 kW at 440 V AC 50/60 Hz (AC-3)75 kW at 500 V AC 50/60 Hz (AC-3)80 kW at 660...690 V AC 50/60 Hz (AC-3)30 kW at 220...230 V AC 50/60 Hz (AC-3)18.5 kW at 400 V AC 50/60 Hz (AC-4) [Uc] control circuit voltage110 V AC 50 Hz Complementary [Uimp] rated impulse withstand voltage8 kV overvoltage categoryIII [Ith] conventional free air thermal current200 A (at 40 °C) rated breaking capacity920 A conforming to IEC 60947-4-1 [Icw] rated short-time withstand current1100 A 40 °C - 10 s640 A 40 °C - 30 s520 A 40 °C - 1 min400 A 40 °C - 3 min320 A 40 °C - 10 min associated fuse rating125 A aM at <= 440 V200 A gG at <= 440 V average impedance0.37 mOhm - Ith 200 A 50 Hz [Ui] rated insulation voltage1000 V conforming to IEC 60947-4-11500 V conforming to VDE 0110 group C power dissipation per pole15 W AC-15 W AC-3 mounting supportPlate standardsEN 60947-4-1IEC 60947-4-1IEC 60947-1JIS C8201-4-1EN 60947-1 product certificationsDNVRMRoSCCCBVABSCBULRINALROS (Lloyds register of shipping) connections - terminalsPower circuit: bar 2 cable(s) - busbar cross section: 20 x 3 mmPower circuit: lugs-ring terminals 1 cable(s) 95 mm²Power circuit: connector 1 cable(s) 95 mm²Control circuit: screw clamp terminals 1 cable(s) 1…4 mm²flexible without cable endControl circuit: screw clamp terminals 2 cable(s) 1…4 mm²flexible without cable endControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²flexible with cable endControl circuit: screw clamp terminals 2 cable(s) 1…2.5 mm²flexible with cable endControl circuit: screw clamp terminals 1 cable(s) 1…4 mm²solid without cable endControl circuit: screw clamp terminals 2 cable(s) 1…4 mm²solid without cable endPower circuit: bolted connection tightening torquePower circuit: 10 N.mControl circuit: 1.2 N.m control circuit voltage limitsOperational: 0.85...1.1 Uc 50/60 Hz (at 55 °C)Drop-out: 0.35...0.55 Uc 50/60 Hz (at 55 °C) inrush power in VA550 VA 50 Hz cos phi 0.3 (at 20 °C) hold-in power consumption in VA45 VA 50 Hz cos phi 0.3 (at 20 °C) heat dissipation12…16 W operating time23...35 ms closing5...15 ms opening mechanical durability10 Mcycles maximum operating rate2400 cyc/h 55 °C compatibility codeLC1F Environment IP degree of protectionIP2x front face with shrouds conforming to IEC 60529IP2x front face with shrouds conforming to VDE 0106 protective treatmentTH ambient air temperature for operation-5…55 °C ambient air temperature for storage-60…80 °C permissible ambient air temperature around the device-40…70 °C operating altitude3000 m without height162 mm width163.3 mm depth171 mm product weight3.43 kg Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS Regulation Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
Documents and DownloadsLanguage
Instruction sheetSizeAdd to My DocumentsCADSizeAdd to My DocumentsTeSys contactors For motor control in utilisation category AC-3 (Version 1.0)CAD file (on TraceParts) for LC1F115F5: TeSys F contactor - 3P (3 NO) - AC-3 - <= 440 V 115 A - coil 110 V AC (Version 2.0)BrochureSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsEnd of Life InformationSizeAdd to My DocumentsMarine certificateSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.