Canalis - straight length - 25 A - 3 m - 2 circuits - 3L+N+PE - whiteShow more characteristics >
Main range of productCanalis product or component typeBusbar trunking product compatibilityKBB Complementary device applicationLightingPower socket distribution radiated magnetic field2 pT [Ue] rated operational voltage230...400 V [Uimp] rated impulse withstand voltage4 kV [Ui] rated insulation voltage690 V [Ie] rated operational current25 A at 35 °C network frequency50/60 Hz [Icw] rated short-time withstand current0.44 kA [Ipk] rated peak withstand current4.4 kA thermal stress limit195 kA².s THDI25 A at 0...15 %20 A at 15...33 %16 A at 33...100 % voltage drop0.72 V with power factor = 1 at 50 Hz with 1A for 100 m long0.67 V with power factor = 0.9 at 50 Hz with 1A for 100 m long0.61 V with power factor = 0.8 at 50 Hz with 1A for 100 m long0.55 V with power factor = 0.7 at 50 Hz with 1A for 100 m long mounting modeBy screws busbar descriptionStraight length busbar trunking polarity3L + N + PE number of circuits2 number of tap-off outlets5 control typeWithout standardsEN/IEC 60439-2EN/IEC 61439-6 width3100 mm depth51 mm height60 mm length3 m colourRAL 9003 : white product weight4.8 kg quantity per setSet of 6 Environment IP degree of protectionIP55 conforming to EN/IEC 60529 IK degree of protectionIK06 conforming to EN/IEC 62262 ambient air temperature for operation0...35 °C at 100 % of In35...40 °C at 96 % of In40...45 °C at 93 % of In45...50 °C at 89 % of In50...55 °C at 85 % of In Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsCADSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.