Main rangeTeSys device short nameGVAE product or component typeAuxiliary contact block product compatibilityGV2LGV2LEGV2MEGV2PGV2RTGV3LGV3PLS1D323 mounting locationFront side pole contact composition1 NO + 1 NC connections - terminalsSpring terminals 2 cable 0.75...1.5 mm² - cable stiffness: flexible - without cable end quantity per setSet of 10 Complementary [Ui] rated insulation voltage300 V - conforming to UL 508300 V - conforming to CSA C22.2 No 14250 V - conforming to IEC 60947-1 [Ue] rated operational voltage24...240 V AC24...60 V DC [Ith] conventional free air thermal current2.5 A protection typeGG fuse 10 AGB2CB06 circuit breaker 10 A mechanical durability100000 cycles minimum switching current5 mA minimum switching voltage17 V rated operational power in VA120 VA at 110...120 V AC-15 - electrical durability: 100000 cycles120 VA at 230...240 V AC-15 - electrical durability: 100000 cycles48 VA at 24 V AC-15 - electrical durability: 100000 cycles60 VA at 48 V AC-15 - electrical durability: 100000 cycles rated operational power in W15 W at 48 V DC-13 - electrical durability: 100000 cycles24 W at 24 V DC-13 - electrical durability: 100000 cycles9 W at 60 V DC-13 - electrical durability: 100000 cycles height13 mm width44.5 mm depth31.5 mm product weight0.05 kg Environment environmental characteristicNormal environment Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsCADSizeAdd to My DocumentsContact blocks for circuit breaker, Instantaneous auxiliary contact blocks (spring terminal connections) (Version 1.0)Instantaneous auxiliary contacts (Version 1.0)CAD files for GVAE113: Instantaneous auxiliary contacts (Version 1.0)
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.