soft starter for asynchronous motor - ATS01 - 85 A - 400 V - 45 KWShow more characteristics >
Main range of productAltistart 01 product or component typeSoft starter product destinationAsynchronous motors product specific applicationSimple machine device short nameATS01 network number of phases3 phases [Us] rated supply voltage400 V - 15...10 % motor power kW45 kW 3 phases 400 V motor power hp50 hp 3 phases 400 V IcL starter rating85 A utilisation categoryAC-53B EN/IEC 60947-4-2 current consumption255 A at nominal load type of startStart with voltage ramp power dissipation in W23 W at full load and at end of starting514 W in transient state Complementary assembly styleWith heat sink function availableIntegrated bypass supply voltage limits340...440 V supply frequency50...60 Hz - 5...5 % network frequency47.5...63 Hz output voltage<= power supply voltage [Uc] control circuit voltageBuilt into the starter starting time1 s 36012 s 30Adjustable from 1 to 25 s deceleration time symbAdjustable from 1 to 25 s starting torque30...80 % of starting torque of motor connected directly on the line supply discrete input typeInternal LI1, LI2, BOOST stop, run and boost on start-up functions <= 8 mA discrete input voltage24 V discrete input logicPositive logic LI1, LI2, BOOST <= 3 V >= 10 V discrete output current2 A DC-133 A AC-15 discrete output typeRelay outputs R1A, R1C discrete output voltage24 V DC relay outputs250 V AC relay outputs minimum switching current10 mA 17 V DC relay outputs display type1 LED green starter powered up1 LED yellow nominal voltage reached tightening torque0.7 N.m5 N.m electrical connectionEarth connection: tinned connector fixed using Ø 6 mm screws4 mm screw clamp terminal rigid 1 6...35 mm² power circuitScrew connector rigid 1 0.75...1.5 mm² control circuit4 mm screw clamp terminal rigid 2 6...25 mm² power circuitScrew connector rigid 2 0.75...1.5 mm² control circuit4 mm screw clamp terminal flexible with cable end 1 4...25 mm² power circuitScrew connector flexible with cable end 1 0.75...1.5 mm² control circuit4 mm screw clamp terminal flexible without cable end 1 6...25 mm² power circuitScrew connector flexible without cable end 1 0.75...1.5 mm² control circuit4 mm screw clamp terminal flexible with cable end 2 4...16 mm² power circuitScrew connector flexible with cable end 2 0.75...1.5 mm² control circuit4 mm screw clamp terminal flexible without cable end 2 6...25 mm² power circuitScrew connector flexible without cable end 2 0.75...1.5 mm² control circuit markingCE operating positionVertical +/- 10 degree height146 mm width180 mm depth126 mm product weight3.8 kg compatibility codeATS01N2 Environment electromagnetic compatibilityDamped oscillating waves level 3 IEC 61000-4-12Electrostatic discharge level 3 IEC 61000-4-2Immunity to electrical transients level 4 IEC 61000-4-4Immunity to radiated radio-electrical interference level 3 IEC 61000-4-3Voltage/current impulse level 3 IEC 61000-4-5Conducted and radiated emissions level B IEC 60947-4-2EMC immunity EN 50082-2Harmonics IEC 1000-3-2Harmonics IEC 1000-3-4Immunity to conducted interference caused by radio-electrical fields level 3 IEC 61000-4-6Micro-cuts and voltage fluctuation IEC 61000-4-11EMC immunity EN 50082-1 standardsEN/IEC 60947-4-2 product certificationsB44.1-96/ASME A17.5 for starter wired to the motor delta terminalCCCCSAC-TickGOSTUL IP degree of protectionIP20 on front panel pollution degree3 IEC 60664-13 UL 508 vibration resistance2 gn shock resistance8 gn 11 ms EN/IEC 60068-2-27 relative humidity5...95 % without condensation or dripping water EN/IEC 60068-2-3 ambient air temperature for operation0...55 °C ambient air temperature for storage-25...70 °C EN/IEC 60947-4-2 operating altitude<= 2000 m without derating> 2000 m with current derating of 0.5 % per additional 100 m Contractual warranty Warranty period18 months
Documents and DownloadsLanguageCADSizeAdd to My DocumentsSoft start/soft stop unit Power : 18.5 to 45 kW - U 3-phase = 230 to 600 V or 400 V
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.