NG125 - earth leakage add-on block - Vigi NG125 - 3P - 63A - 30mAShow more characteristics >
Main product or component typeAdd-on residual current devices device short nameVigi NG125 poles description3P [In] rated current63 A network typeAC earth-leakage sensitivity30 mA earth-leakage protection time delayInstantaneous earth-leakage protection classType A Complementary device location in systemOutgoer network frequency50/60 Hz [Ue] rated operational voltage230...415 V AC 50/60 Hz residual current tripping technologyVoltage independent [Ui] rated insulation voltageAC 50/60 Hz conforming to IEC 60947-2 [Uimp] rated impulse withstand voltage8 kV conforming to IEC 60947-2 mounting support35 mm symmetrical DIN rail electrical connection to mcbBy screws 9 mm pitches9 height118 mm width162 mm depth81 mm product weight0.41 kg electrical durability10000 cycles conforming to IEC 60947-2 connections - terminalsTunnel type terminals1…35 mm² flexibleTunnel type terminals1.5…50 mm² rigid wire stripping length20 mm tightening torque3.5 N.m Environment standardsIEC 60947-2 IP degree of protectionIP40 conforming to IEC 60947-2 pollution degree3 conforming to IEC 60947-2 electromagnetic compatibility8/20 µs impulse withstand, 3000 A conforming to IEC 60947-2 tropicalisation2 conforming to IEC 60068-1 relative humidity95 % at 55 °C operating altitude2000 m Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS Regulation Environmental Disclosure Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
Documents and DownloadsLanguage
CADSizeAdd to My DocumentsEnd of Life InformationSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.