residual current circuit breaker ID - 4 poles - 63 A - class B 30 mAShow more characteristics >
Main rangeActi 9 product nameActi 9 RCCB-ID product or component typeResidual current circuit breaker (RCCB) device short nameRCCB-ID poles description4P neutral positionLeft [In] rated current63 A network typeAC earth-leakage sensitivity30 mA earth-leakage protection time delayInstantaneous earth-leakage protection classType B rated breaking and making capacityIm 630 A conforming to IEC 61008 rated conditional short-circuit currentInc 10 kA 63 A Complementary device location in systemOutgoer network frequency50/60 Hz [Ue] rated operational voltage230/400 V [Ui] rated insulation voltage440 V AC 50 Hz conforming to IEC 61008-1 [Uimp] rated impulse withstand voltage4 kV conforming to IEC 61008-1 connection pitch18 mm : Between phases 9 mm pitches8 height86 mm width72 mm depth76 mm product weight450 g colourGrey mechanical durability5000 cycles electrical durability2000 cycles connections - terminalsTunnel type terminals 1 cable(s) 1.5...50 mm² rigidTunnel type terminals 1 cable(s) 1.5...35 mm² flexibleTunnel type terminals 1 cable(s) 1.5...35 mm² flexible with ferruleTunnel type terminals 2 cable(s) 1.5...16 mm² flexible with ferruleTunnel type terminals 2 cable(s) 1.5...16 mm² flexibleTunnel type terminals 2 cable(s) 1.5...16 mm² rigid wire stripping length11 mm tightening torque3 N.m Environment standardsVDE 0664EN 61008IEC 61008 IP degree of protectionIP40 in modular enclosure conforming to IEC 60529IP20 conforming to IEC 60529 tropicalisation2 relative humidity95 % ( 55 °C ) ambient air temperature for operation-25...40 °C ambient air temperature for storage-40...85 °C Offer Sustainability RoHS (date code: YYWW) REACh Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CADSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.