|FA23093||What is the degree of protection of 27046, 27047 and 27048 rotary handles.|
The degree of protection of rotary handles references 27046, 27047 and 27048 is IP40.
These rotary handles are designed for C60, C120 and NC100 circuit...
|FA22993||What is the ratio n between the peak value and the root mean square value of the short-circuit current|
Product standard BS EN 60947-1 defines the ratio n between the peak value and the rms value of the short-circuit current (table 16 on page 106). The...
|FA23005||What are the characteristics of phase unbalance protection of STR22ME and STR43ME motor trip units for NS100 to 630 circuit-breakers|
STR22ME and STR43ME electronic motor trip units incorporate protection against phase unbalance (current).
For the STR22ME trip unit: the unit compares...
|FA23865||How can I fit the shunt trip MX or undervoltage MN coil on a Compact NS100 to 630.|
Please see the attached instructions.
The MCCB must be in the tripped position before fitting / removing shunt trip or undervolatge coils.
|FA142622||Tripping curves for GB2 circuit breakers.|
The tripping curves for the GB2 circuit breakers are displayed below :
Extracted from the Control and protection components 2011/2012 catalogue...
|FA141663||Where can I find additional XU multimode photo electric sensor set up and diagnostics information?|
The XU multi mode (also known as Osiconcept , OsiSense and Osiris) photo electric sensors can be configured for 4 different modes of operation.
|FA27986||Can I connect aluminium or copper, flexible or rigid cables to the single and double terminals of the NSX 400 to 630 range.|
In the NSX 400 to 630 range:
Single terminals, part numbers LV432479 or LV432480, can take: aluminium or copper rigid cables with cross-section 35...
|FA22985||How can I find a lost code on Sepam 2000?|
To find the lost code on a Sepam 2000 prior to 96/49:
go to the control logic in which the code (password) is given
To find the lost code of a...
|FA23007||What is the meaning of the items screen-printed on the setting selector switches of the Micrologic and STR electronic control units.|
Standard IEC 60947-2 defines the names of the selector switches.
The meanings of the screen-printed items on the selector switches of the trip units...
|FA33574||What is the default password for the Sepam relays?|
The password for Sepam 20, 40 and 80 is:- 0000
The password for Sepam 2000 is:- 6543210