|FA243314||Do ION7550, ION7650 and ION8800 comply with CoP 1- 2 and 3?|
Yes they do, please check the attached certificate
|FA132872||What is the IP rating of RM6|
RM6 has an IP rating of IP3X on the front face and the gas tank is rated at IP67.
For more information on RM6 please click here or e-mail: firstname.lastname@example.org...
|FA23919||What are the values of the 1P breaking capacities of GV2P circuit-breakers in IT earthing system?|
The values below are the breaking capacities of GV2P circuit-breakers operating on an IT earthing system at 400 V 50 Hz, as demonstrated by pole-by-pole...
|FA23898||How can I cable an Emergency Stop with ATV312 (or ATV31)?|
The ATV312 (or ATV31) drive does not have a dedicated safety terminal recognized by the machine safety regulations.
If the machine has to be made...
|FA28029||What is the difference between a beacon with flashing signals and a beacon with a flash discharge tube?|
The light perception of a beacon with Flash discharge tube is different from a beacon with blinking signals.
The difference between these two technologies...
|FA23719||What are the differences between emergency stop and emergency switching-off pushbuttons?|
The Schneider offer includes two types of pushbutton.
a) Emergency switching-off with mechanical latching
These have direct opening action.
|FA28044||What adaptation parts satisfy standard UL 508 type E on the GV2P and GV3P?|
The adaptation parts to be used so that GV2P and GV3P circuit breakers comply with standard UL 508 type E are detailed below.
For GV2P circuit breakers:
|FA28058||To what standards do the A class and B class filters correspond in the variable speed drives?|
EMC environment and EMC input filter
Industrial and commercial EMC environments are described by standards, and Schneider Electric has designed EMC...
|FA32998||What is the temperature rise level of the GV2Pxx and what does the standard say?|
Tests on GV2 circuit breakers are carried out in accordance with IEC 94741, usually in the enclosure because there is a dedicated enclosure.
|FA136111||Does Schneider Electric offer 'safety contactors'?|
The term 'safety contactor' does not appear to have any clear definition within the Safety of Machinery standard IEC (BS EN) 60204-1 or within IEC...