|FA31963||If the C120H circuit breaker is locked ON with the 27145 padlocking facility will it still trip under fault conditions.|
Yes, All of the miniature circuit breakers have a "trip free" mechanism which enables them to trip under fault conditions even if the handle is locked...
|FA23786||Can the SDE contact be fitted into a Masterpact NT or NW switch disconnector.|
The SDE contact does not perform any function on a Masterpact switch disconnector and therefore it's not fitted nor is it available as an option.
|FA23865||How can I fit the shunt trip MX or undervoltage MN coil on a Compact NS100 to 630.|
Please see the attached instructions.
The MCCB must be in the tripped position before fitting / removing shunt trip or undervolatge coils.
|FA23748||What is the part number of the fixed Front Connection snap-in nuts for the Compact NS100 to 630 circuit-breakers.|
The part number of a set of 12 fixed front connection snap-in nuts is:
29234 for Compact NS100.
30554 for Compact NS160... 250.
These parts are...
|FA142687||What is the difference between an LUB12 32 & LUB120 320 Tesys U starter?|
The Tesys U non reversing starter controller offers two types of power base units in its range
LUB12 & LUB120 (0 – 12A, 5.5kw at 400V)
LUB32 & LUB320...
|FA142680||What equipment uses the TSXCUSB485 USB converter?|
Here are some of our products that use this USB converter:
XPSMC safety modules
TSX Micro PLC’s
|FA142425||Is there an enclosure for GV3, to make an enclosed starter? Can we fit GV3P, GV3L and GV3ME? Can we mount LC1 contactor?|
Yes, there is an enclosure that can take the new GV3P and GV3L, plus there’s space to mount a contactor inside.
The new enclosures GV3PC aren’t suitable...
|FA142666||What is the difference between an LADR1V and LADR1 reversing contactor kit?|
The difference is the LADR1V kit has mechanical & electrical interlocking, where the LADR1 has only mechanical interlock.
See below for what the...
|FA142116||Do LC1K and LC1D have mirror contacts? Which ones are those?|
Yes, if those contactors have built in or using ad on auxiliary, in the following circumstances:
TESYS model K contactors :
|FA141635||Can I connect an SR2 or SR3 Zelio Logic Smart Relay to an HMI, separate display screen?|
Yes, you can connect the SR2 or SR3 to a small HMI, this HMI comes included in a kit, starter-kit HMISTO & Zelio Logic – reference: VJDSTKSTOSR2