|FA139220||What replaced XPSAL? What are the differences between XPSAL and the new XPSAC?|
XPS-AL Replaced by XPS-AC
XPSAL (old model) XPSAC (new model)
XPS-AC has one...
|FA139510||Can you suggest an easy way to make a single phase combination motor starter with protection?|
For single phase motors with a small kW rating the following combinations may be suitable:
GB2DB##SK** - Single phase combination motor starters
|FA23787||How can I lock the direct rotary handle on a Compact NS400 / NS630 circuit-breaker.|
The direct rotary handle can either be locked with padlocks or a keylock.
Locking with Padlocks:
Up to three padlocks can be fitted. The shackle...
|FA23093||What is the degree of protection of 27046, 27047 and 27048 rotary handles.|
The degree of protection of rotary handles references 27046, 27047 and 27048 is IP40.
These rotary handles are designed for C60, C120 and NC100 circuit...
|FA23749||What is the tightening torque for the terminal extensions and spreaders for Compact NS100 to 630 circuit-breakers.|
The tightening torque for the terminal extensions and spreaders for Compact NS100 to 630 circuit breakers is:
10 Nm for Compact NS100.
15 Nm for...
|FA31963||If the C120H circuit breaker is locked ON with the 27145 padlocking facility will it still trip under fault conditions.|
Yes, All of the miniature circuit breakers have a "trip free" mechanism which enables them to trip under fault conditions even if the handle is locked...
|FA23786||Can the SDE contact be fitted into a Masterpact NT or NW switch disconnector.|
The SDE contact does not perform any function on a Masterpact switch disconnector and therefore it's not fitted nor is it available as an option.
|FA23865||How can I fit the shunt trip MX or undervoltage MN coil on a Compact NS100 to 630.|
Please see the attached instructions.
The MCCB must be in the tripped position before fitting / removing shunt trip or undervolatge coils.
|FA23748||What is the part number of the fixed Front Connection snap-in nuts for the Compact NS100 to 630 circuit-breakers.|
The part number of a set of 12 fixed front connection snap-in nuts is:
29234 for Compact NS100.
30554 for Compact NS160... 250.
These parts are...
|FA142687||What is the difference between an LUB12 32 & LUB120 320 Tesys U starter?|
The Tesys U non reversing starter controller offers two types of power base units in its range
LUB12 & LUB120 (0 – 12A, 5.5kw at 400V)
LUB32 & LUB320...