|FA27927||Can I use the 63A 3P busbars of the GV2 range on the Tesys U range?|
The 63 A 3-pole busbars are identical for pre-wiring several modules of the following type:
GV2 circuit breakers
|FA22688||What is the part number of the pad lockable external handle to be adapted to a GV2LE?|
For the GV2LE circuit-breaker, one part number can be used: GV2AP03
|FA23827||What is the difference between the LAD93217 and LAD93218 kits and between the LAD91217 and LAD91218 kits?|
The star-delta kits part numbers LAD91217 and LAD91218 are designed for LC3D09, LC3D09A, LC3D12 and LC3D12A star-delta starters.
|FA28059||Can I place a TeSys U starter-controller downstream from a variable speed drive?|
TeSys U controllers fitted with an LUCLxxxx control units are ideal for protecting drive/motor or starter/motor assemblies, but can only be installed...
|FA24892||How can I distinguish thermal from magnetic faults when using GV2ME, GV2P, GV2L and GV2LE?|
Using a GVAM11 combined with a GVAD10xx, it is possible to distinguish between thermal and and magnetic faults.
If there is no fault:
|FA28044||What adaptation parts satisfy standard UL 508 type E on the GV2P and GV3P?|
The adaptation parts to be used so that GV2P and GV3P circuit breakers comply with standard UL 508 type E are detailed below.
For GV2P circuit breakers:
|FA24910||What is the difference between the XPSMF4040, XPSMF4042 and the XPSMF4020, XPSMF4022 type Preventa programmable compact safety PLCs?|
XPSMF40 types XPSMF4040 and XPSMF4042 safety PLCs have a Profibus DP communication interface for transferring non-safety data. The connection is a...
|FA22943||How do I connect a potentiometer on time delay relays part numbers: RE7TM, TP, MA, RA, RM, PP, PM,ML or MY?|
When using RE7 TM, TP, MA, RA, RM, PP, PM,ML or MY relays with time delay adjustment potentiometers, these potentiometers must be connected in the...
|FA24941||Can I install simultaneously a ZBZ48 bellow seal and a ZBZ1604 metal guard rail on an emergency stop pushbutton?|
It is not possible to install the ZBZ160x metal guard rail & ZBZ48 bellows seal for harsh environments simultaneously on Harmony XB4 and XB5 emergency...
|FA23899||Is a motor choke necessary when using a Lexium 15?|
Motor chokes are mandatory for drive-motor cables more than 25 metres long.They reduce current ripple and protect the output stage of the servo drive.