Free and available to all electricians - find the information you need, digital tools to support your business and more.Electrician portal
New, connected, and future ready.Are you ready?
Browse our catalogue of over 200 FREE e-learning courses.Start learning today
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Receive all the latest updates, news, and offers via Twitter.Follow us on Twitter
Schneider Electric United Kingdom Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
|There is a risk of condensation when air around KT /KH conductors is cooling.
For example, for humidity = 50% and ambient temperature at 50°C around working conductors. When the power disappears, the ambient temperature will be <37°C, and the humidity in the air starts to condense. This is called : dew point.
From 37°C to 4°C (ambient temperature), the condensation will increase:
- During this time:
In conclusion :
- when KT or KH are running without any turn off, there is a thermal balance, therefore no condensation means no risk.
- If busway must be turned off for long time, it's necessary to have a security process before re-starting :
check for the prescence of humidity, if yes, carry out preventive drying and check the insulating resistances (IEC 60439-1 & 8.3.4)for further assistance regarding insulating test , starting after water damage please contact the Canalis technical team on 0870 608 8 608