New, connected, and future ready.Are you ready?
Browse our catalogue of over 200 FREE e-learning courses.Start learning today
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Receive all the latest updates, news, and offers via Twitter.Follow us on Twitter
Schneider Electric United Kingdom Website×
It's normal that the ref A9V02763 trips in a longer time than the old multi9 MGV630304 because it's A type vigi unit
This new RCD uses "ACCU" technology which is better on continuity of service however the tripping time is higher.
The ref 26665 "old Multi9" is AC type low continuity of service with "AD or CSP" technology !
If a tripping of less than 100ms is required then please use MCB in conjunction with a AC type RCD