Free and available to all electricians - find the information you need, digital tools to support your business and more.Electrician portal
New, connected, and future ready.Are you ready?
Browse our catalogue of over 200 FREE e-learning courses.Start learning today
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Receive all the latest updates, news, and offers via Twitter.Follow us on Twitter
Schneider Electric United Kingdom Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The R1 relay output for ATS01 indicates that the motor is being controlled by the soft start and is in a running state. It is a normally open contact which closes on the start of ramp and opens when the end of ramp is reached.
It does not indicate a product or application fault as there is no fault or overload detection within the ATS01 series softstarts.
The marking of the R1 relay contacts differ according to the part number of the unit.
The terminals are marked as R1A and R1C for most ATS01 starters apart from ATS01N2**LY/Q variants where the terminals are marked as 04 and 05.
This relay can be used in a number of different ways:
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!