New, connected, and future ready.Are you ready?
Browse our catalogue of over 200 FREE e-learning courses.Start learning today
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Receive all the latest updates, news, and offers via Twitter.Follow us on Twitter
Schneider Electric United Kingdom Website×
Using a GVAM11 combined with a GVAD10xx, it is possible to distinguish between thermal and and magnetic faults.
Test for correct operation
The instantaneous auxiliary contact test is performed by creating a state of transition of the handle actuator between the de-energised position and the energised position.
The fault contact test is performed by pressing the test button when the handle actuator is in the closed position.