New, connected, and future ready.Are you ready?
Browse our catalogue of over 200 FREE e-learning courses.Start learning today
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Receive all the latest updates, news, and offers via Twitter.Follow us on Twitter
Schneider Electric United Kingdom Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
No. There are two reasons preventing a potentiometer, part number SZ1RV1202, from being installed in an XACA enclosure:
1. An SZ1RV1202 potentiometer requires a 10.5 mm drill hole for installation, whereas the enclosure has a 22.2 mm drill hole
2. The intermediate metal contact fixing plate does not leave enough space below the front panel for the potentiometer body
Solution: Use the XACB or XACM boxes with ZB5AD912 (6mm potentiometer shaft) or ZB5AD922 (6.35mm, 1/4" shaft).
It is necessary for the user to supply the potentiometer as it is not supplied with the heads. The potentiometer should be 2.2K Ohm linear, with a shaft length of 45 to 50mm. A rating of 2 Watts is recommended for VSD applications though 1/2 Watt or more should be fine and will be much more compact.