Free and available to all electricians - find the information you need, digital tools to support your business and more.Electrician portal
New, connected, and future ready.Are you ready?
Browse our catalogue of over 200 FREE e-learning courses.Start learning today
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Receive all the latest updates, news, and offers via Twitter.Follow us on Twitter
Schneider Electric United Kingdom Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
There is no published scheme for creating a star delta using Tesys U componentry but it can be creating by the addition of some non Tesys U parts, contactors etc.
It is also possible to construct a reversing star delta using 2 Tesys U stand alone reversing units LU6MB0** plus 2 additional contactors.
In both scenarios the Tesys U is upstream of the delta loop, therefore the maximum motor sizes are limited to 12A FLC and 32A FLC for LUB12 and LUB32 respectively.
Please see the attached documents for schematics of possible scheme.
These are functional schematic diagrams to illustrate how the control can be achieved. The installer remains responsible for ensuring all relevant local legislation and directives are met and that suitable circuit protection is provided.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!