Free and available to all electricians - find the information you need, digital tools to support your business and more.Electrican portal
New, connected, and future ready.Are you ready?
Browse our catalogue of over 200 FREE e-learning courses.Start learning today
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Receive all the latest updates, news, and offers via Twitter.Follow us on Twitter
Schneider Electric United Kingdom Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The total heat loss of a Liquid Filled (Insulation Class "A") Power Distribution Transformer at various loads is calculated as follows :-
At 100% load the total heat loss is the addition of the No Load Loss and the Load Loss
At X% load, the total heat loss is (X/100)² x Load Loss at 100% Load + No Load Loss
i.e. The No Load Loss is a constant loss and does not change with load
The Load Loss varies to the square of the per unit load
e.g. 1000kVA transformer with a No Load Loss of 1340 Watts and a Load Loss of 12500 Watts at 100% load and reference temperature of 75ºC, has the following losses at various loads