Free and available to all electricians - find the information you need, digital tools to support your business and more.Electrician portal
New, connected, and future ready.Are you ready?
Browse our catalogue of over 200 FREE e-learning courses.Start learning today
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Receive all the latest updates, news, and offers via Twitter.Follow us on Twitter
Schneider Electric United Kingdom Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
With regard to cooling of air-cooled transformers the temperature conditions at the intended installation site should neither exceed :-
+30ºC monthly average, of the hottest month: nor
+20ºC yearly average.
The above figures are based on the transformer installation site being less then 1000m above sea level.
If the transformer is required to operate at higher ambient temperatures and/or higher altitudes, then the transformer would need to be designed specially for the intended application
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!